Telecommunication cable is predominantly used in electrical instrumentation and communications. The cable is manufactured to specification ENATS 09-6 Section 4.5. (Electrical National Association and Technical specification). ENATS is the governing body who cover utilities specification cables.
Conductor: Solid Plain Annealed CopperConductors
Insulation: Low Smoke Zero Halogen (LSZH)
Bedding: Low Smoke Zero Halogen (LSZH)
Armouring: Galvanised Steel Wire Armour
Sheath: Low Smoke Zero Halogen (LSZH)
Sheath Colour: Black
**All two pair cables are in quad formation
Voltage Rating: 110 Volts
Temperature Limits: -20°C to +70°C
Minimum Bending Radius: As per cable manufacturer datasheet
Should not be installed at temperatures below 0°C or above +40°C
For more information please consult a member of the Cleveland Cable Sales Team
See datasheet PDF for further details
**All two pair cables are in quad formation and colour coded in rotation
White Red Blue Orange
For 30 pair cables the formation will be 3 X 10 pair units numbered - 1, 2 & 3.
For 40 pair cables the formation will be 2 X 20 pair units numbered - 1 & 2.
For 50 pair cables the formation will be 5 X 10 pair units numbered - 1, 2 3, 4 & 5.
For 100 pair cables the formation will be 5 X 20 pair units numbered - 1, 2, 3, 4 & 5.
|Code||Description||Qty / Metres|
|13501||2 CORE LSZH, SWA, LSZH, ENATS 09-6, BLACK|
|13503||5 CORE LSZH, SWA, LSZH, ENATS 09-6, BLACK|
|13504||10 CORE, LSZH, SWA, LSZH, ENATS 09-6, BLACK|
|13506||20 CORE, LSZH, SWA, LSZH, ENATS 09-6, BLACK|
|13510||50 CORE, LSZH, SWA, LSZH, ENATS 09-6, BLACK|
|13511||100 CORE, LSZH, SWA, LSZH, ENATS 09-6, BLACK|
Registered Office: Riverside Park Road, Middlesbrough, Cleveland, TS2 1QW
Place of Registration: England | Registered number: 5538824